Flextronics Product Center
Yancheng Flextronics Electric Heating Equipment Technology Co., Ltd. Contact: Mr. Jiang Tel: 0515-83063266
Address: Chaoyang Road, Yifeng Industrial Park, Dazonghu Town, Yandu District, Yancheng City, Jiangsu Province Post Code: 224000
Your current location ： Home>
- What to pay attention to when designing the heating oil heating furnace device
- 9/19/2017 Views: 
- ① Set a high-profile exhaust pipe with a valve in the heating system, install a sewage facility at the lower position of the heater, and regularly discharge the deposits, gums, and carbon residues generated after the thermal oil is decomposed at high temperature;② Expansion tank (tank) is an indispensable part of the heating device. According to the amount of thermal oil in the entire heating system, plus the expansion coefficient, design the size and position of the expansion tank (tank). If the exhaust pipe is designed on the expansion tank (tank) , Consider the use of inert gas seal or exhaust gas valve switch operation problem, the heat transfer oil in the tank (tank) should not be less than 1/3 of the volume when using;③ Use high temperature, oil and pressure resistant gaskets in the closed heating cycle system to prevent hot oil from leaking, and set a bypass filter in the system;④ The designer should pay attention to the heating structure of the heater, so that the heat transfer oil does not overheat locally; the temperature difference between the heat transfer oil inlet and outlet should be within the range of 20 ～ 40 ℃, the flow rate of the low temperature oil should be greater than 2m / s, and the return pipe of the heat transfer oil It should be located at a low position of 20-25cm from the heater. At the same time, a pressure gauge and a flow meter should be installed at the inlet and outlet of the thermal oil, and a thermometer should be installed at the inlet and outlet and the heater.
- Next: How to judge the quality of electric heating pipe